AixLib.Obsolete.Year2024.Fluid.HeatExchangers.EvaporatorCondenserWithCapacity

# .AixLib.Obsolete.Year2024.Fluid.HeatExchangers.EvaporatorCondenserWithCapacity

## Information

#### Deprecation Warning

This model is deprecated, use AixLib.Fluid.HeatPumps.ModularReversible.BaseClasses.EvaporatorCondenserWithCapacity instead.

Model for an evaporator or condenser with the use of a capacity to simulate heat losses.

Used in AixLib.Obsolete.Year2024.Fluid.HeatPumps.HeatPump, the heat flow to or from the volume is calculated in a black box. Thus the heat is directly added to the medium.

In order to model transient states and inertias of a real heat pump, a capacity is added to the base model TwoPortHeatMassExchanger.

The heat exchange between capacity and medium (GIns) is based on a series of heat resistances caused by forced convection and conduction through the capacity of the heat exchanger. Losses or gains in result of heat exchange with the ambient are modeled through the heat exchange coefficient GOut is represented by a series of conductive resistances and the convection to the ambient.

Both parameters GIns and GOut are variable so that the calculation can follow a temperature or flow-rate based approach.

## Revisions

- November 26, 2018 by Fabian Wüllhorst:
  First implementation (see issue #577)

Generated at 2026-05-09T18:18:56Z by OpenModelicaOpenModelica 1.26.7 using GenerateDoc.mos