AixLib.Fluid.FixedResistances.Validation.PlugFlowPipes.MSLAIT

# .AixLib.Fluid.FixedResistances.Validation.PlugFlowPipes.MSLAIT

Validation pipe against data from Austrian Institute of Technology with standard library components

## Information

The example contains experimental data from a real district heating network. This data is used to validate this library's AixLib.Fluid.FixedResistances.PlugFlowPipe in AixLib.Fluid.FixedResistances.Validation.PlugFlowPipes.PlugFlowAIT. This model compares its performance with the original Modelica Standard Library pipes, using one discretization element per unit length of pipe. For a coarser discretization, please refer to MSLAIT2Nodes.

Note that these three models are identical, except for the pipe model that is used:

- The model AixLib.Fluid.FixedResistances.Validation.PlugFlowPipes.MSLAIT uses the pipe model from the Modelica Standard Library, with a fine discretization. See the parameter `nNodes`.
- The model AixLib.Fluid.FixedResistances.Validation.PlugFlowPipes.MSLAIT2Nodes uses the same model as above, but sets `nNodes=2`.
- The model AixLib.Fluid.FixedResistances.Validation.PlugFlowPipes.PlugFlowAIT uses the plug flow model AixLib.Fluid.FixedResistances.PlugFlowPipe.

This comparison between different discretization levels and pipe models is made to check the influence of the discretization and pipe model on computation time and simulation accuracy.

The pipes' temperatures are not initialized, thus results of outflow temperature before approximately the first 10000 seconds should not be considered.

#### Test bench schematic

#### Calibration

To calculate the length specific thermal resistance `R` of the pipe, the thermal resistance of the surrounding ground is added.

R=1/(0.208)+1/(2 lambda_g Modelica.Constants.pi) log(1/0.18)

Where the thermal conductivity of the ground `lambda_g` = 2.4 W/(m K).

## Contents

Name | Description
--- | ---
Medium |

## Revisions

- March 7, 2020, by Michael Wetter:
  Replaced measured data from specification in Modelica file to external table, as this reduces the computing time.
  This is for #1289.
- May 15, 2019, by Jianjun Hu:
  Replaced fluid source. This is for #1072.
- November 28, 2016 by Bram van der Heijde:
  Remove `pipVol.`
- August 24, 2016 by Bram van der Heijde:
  Implement validation with MSL pipes for comparison, based on AIT validation.
- July 4, 2016 by Bram van der Heijde:
  Added parameters to test the influence of allowFlowReversal and the presence of explicit volumes in the pipe.
- January 26, 2016 by Carles Ribas:
  First implementation.

Generated at 2026-05-09T18:18:56Z by OpenModelicaOpenModelica 1.26.7 using GenerateDoc.mos