BuildingSystems.Fluid.HeatPumps.Data.ScrollWaterToWater.Heating.Daikin_WRA420_137kW_4_50COP_R410A

# .BuildingSystems.Fluid.HeatPumps.Data.ScrollWaterToWater.Heating.Daikin_WRA420_137kW_4_50COP_R410A

Calibrated parameters for Daikin WRA420

## Information

Calibrated parameters for Daikin WRA420.

#### Definition

>     record Daikin_WRA420_137kW_4_50COP_R410A = BuildingSystems.Fluid.HeatPumps.Data.ScrollWaterToWater.Generic(volRat = 2.31768014295, V_flow_nominal = 0.0151967313394, leaCoe = 0.0108643581925, etaEle = 0.749270140609, PLos = 6263.77526408, dTSup = 10.0, UACon = 24801.5921552, UAEva = 297902.470363);

## Revisions

- March 6, 2017, by Massimo Cimmino:
  Calibrated parameters.

Generated at 2026-05-09T18:18:56Z by OpenModelicaOpenModelica 1.26.7 using GenerateDoc.mos